A smoke detector is a device that senses smoke, typically as an indicator of fire. Commercial smoke detectors issue a signal to a fire alarm control panel as part of a fire alarm system, while household smoke detectors, also known as smoke alarms, generally issue an audible or visual alarm from the detector itself or several detectors if there are multiple smoke detectors interlinked.
Smoke detectors are housed in plastic enclosures, typically shaped like a disk about 150 millimetres (6 in) in diameter and 25 millimetres (1 in) thick, but shape and size vary. Smoke can be detected either optically (photoelectric) or by physical process (ionization). Detectors may use one of the two, or both sensing methods. Sensitive alarms can be used to detect, and deter, people smoking in areas where smoking is banned. Smoke detectors in large commercial and industrial buildings are usually connected to a central fire alarm system. Domestic smoke detectors range from individual battery powered units to several interlinked units with battery backup. With interlinked units, if any of them detect smoke, all of the alarms will trigger even if household power has gone out.
The risk of dying in a home fire is cut in half in homes with working smoke alarms. The US National Fire Protection Association reports 0.53 deaths per 100 fires in homes with working smoke alarms compared to 1.18 deaths without (2009–2013). Some homes do not have any smoke alarms and some homes do not have any working batteries in their smoke alarms.
The first automatic electric fire alarm was patented in 1890 by Francis Robbins Upton, an associate of Thomas Edison. George Andrew Darby patented the first European electrical heat detector in 1902 in Birmingham, England. In the late 1930s Swiss physicist Walter Jaeger tried to invent a sensor for poison gas. He expected that gas entering the sensor would bind to ionized air molecules and thereby alter an electric current in a circuit in the instrument. His device did not meet its purpose: small concentrations of gas did not affect the sensor's conductivity. Frustrated, Jaeger lit a cigarette and was soon surprised to notice that a meter on the instrument had registered a drop in current. Smoke particles from his cigarette had done what poison gas could not. Jaeger's experiment was one of the advances that paved the way for the modern smoke detector. In 1939 Swiss physicist Ernst Meili devised an ionization chamber device capable of detecting combustible gases in mines. He also invented a cold cathode tube that could amplify the small signal generated by the detection mechanism to a strength sufficient to activate an alarm.
Ionization smoke detectors were first sold in the United States in 1951; they were used only in major commercial and industrial facilities in the next several years due to their large size and cost. In 1955 simple home "fire detectors" for homes were developed, detecting high temperatures. The United States Atomic Energy Commission (USAEC) granted the first license to distribute smoke detectors using radioactive material in 1963. The first low-cost smoke detector for domestic use was developed by Duane D. Pearsall with Stanley Bennett Peterson in 1965, an individual replaceable battery-powered unit that could be easily installed. The "SmokeGard 700" was a beehive-shaped, strong fire-resistant steel unit. The company began mass-producing these units in 1975. Studies in the 1960s determined that smoke detectors respond to fires much faster than heat detectors.
The first single-station smoke detector was invented in 1970 and made public the next year. It was an ionization detector powered by a single 9-volt battery. They cost about US$125 and sold at a rate of a few hundred thousand per year. Several technological developments occurred between 1971 and 1976, including the replacement of cold-cathode tubes with solid-state electronics, which greatly reduced the detectors' cost and size, and made it possible to monitor battery life. The previous alarm horns, which required specialty batteries, were replaced with horns that were more energy-efficient, enabling the use of commonly available batteries. These detectors could also function with smaller amounts of radioactive source material, and the sensing chamber and smoke detector enclosure were redesigned for more effective operation. The rechargeable batteries were often replaced by a pair of AA batteries along with a plastic shell encasing the detector. The 10-year-lithium-battery-powered smoke alarm was introduced in 1995.
The photoelectric (optical) smoke detector was invented by Donald Steele and Robert Emmark of Electro Signal Lab and patented in 1972.
An ionization smoke detector uses a radioisotope, typically americium-241, to ionize air; a difference due to smoke is detected and an alarm is generated. Ionization detectors are more sensitive to the flaming stage of fires than optical detectors, while optical detectors are more sensitive to fires in the early smouldering stage.
The smoke detector has two ionization chambers, one open to the air, and a reference chamber which does not allow the entry of particles. The radioactive source emits alpha particles into both chambers, which ionizes some air molecules. There is a potential difference (voltage) between pairs of electrodes in the chambers; the electrical charge on the ions allows an electric current to flow. The currents in both chambers should be the same as they are equally affected by air pressure, temperature, and the ageing of the source. If any smoke particles enter the open chamber, some of the ions will attach to the particles and not be available to carry the current in that chamber. An electronic circuit detects that a current difference has developed between the open and sealed chambers, and sounds the alarm. The circuitry also monitors the battery used to supply or back up power, and sounds an intermittent warning when it nears exhaustion. A user-operated test button simulates an imbalance between the ionization chambers, and sounds the alarm if and only if power supply, electronics, and alarm device are functional. The current drawn by an ionization smoke detector is low enough for a small battery used as sole or backup power supply to be able to provide power for months or years without the need for external wiring.
Ionization smoke detectors are usually cheaper to manufacture than optical detectors. They may be more prone to false alarms triggered by non-hazardous events than photoelectric detectors, and are much slower to respond to typical house fires.
Americium-241 is an alpha emitter with a half-life of 432.6 years. Alpha particle radiation, as opposed to beta (electron) and gamma (electromagnetic) radiation, is used for two reasons: alpha particles have more ionizing power, so as to ionize enough air to make a detectable current, and they have low penetrative power, meaning they will be stopped, safely, by the plastic of the smoke detector or the air. About one percent of the emitted radioactive energy of 241Am is gamma radiation. The amount of elemental americium-241 is small enough to be exempt from the regulations applied to larger deployments. A smoke detector contains about 37 kBq or 1 µCi of radioactive element americium-241 (241Am), corresponding to about 0.3 µg of the isotope. This provides sufficient ion current to detect smoke, while producing a very low level of radiation outside the device.
The americium-241 in ionizing smoke detectors poses a potential environmental hazard, albeit a very small one. Disposal regulations and recommendations for smoke detectors vary from region to region. The amount of radioactive material contained in ionizing smoke detectors is very small and thus doesn't represent a significant radiological hazard. If the americium is left in the ionization chamber of the alarm the radiological risk is insignificant because the chamber acts as a shield to the alpha radiation. A person would have to open the sealed chamber and ingest or inhale the americium for the risk to be significant. The radiation risk of exposure to an ionic smoke detector operating normally is much smaller than natural background radiation.
Some European countries, including France, and some US states and municipalities have banned the use of domestic ionic smoke alarms because of concerns that they are not reliable enough as compared to other technologies. Where an ionizing smoke detector has been the only detector, fires in the early stages have not always been effectively detected.
This section needs additional citations for verification. (August 2016)
A photoelectric, or optical smoke detector, contains a source of infrared, visible, or ultraviolet light — typically an incandescent light bulb or light-emitting diode (LED) — a lens, and a photoelectric receiver — typically a photodiode. In spot-type detectors, all of these components are arranged inside a chamber where air, which may contain smoke from a nearby fire, flows. In large open areas such as atria and auditoriums, optical beam or projected-beam smoke detectors are used instead of a chamber within the unit: a wall-mounted unit emits a beam of infrared or ultraviolet light which is either received and processed by a separate device or reflected to the receiver by a reflector. In some types, particularly optical beam types, the light emitted by the light source passes through the air being tested, and reaches the photosensor. The received light intensity will be reduced due to scattering from particulates of smoke, air-borne dust, or other substances; the circuitry detects the light intensity and generates the alarm if it is below a specified threshold, potentially due to smoke. In other types, typically chamber types, the light is not directed at the sensor, which is not illuminated in the absence of particles. If the air in the chamber contains particles (smoke or dust), the light is scattered and some of it reaches the sensor, triggering the alarm.
According to the National Fire Protection Association (NFPA), "photoelectric smoke detection is generally more responsive to fires that begin with a long period of smoldering". Studies by Texas A&M and the NFPA cited by the City of Palo Alto, California state, "Photoelectric alarms react slower to rapidly growing fires than ionization alarms, but laboratory and field tests have shown that photoelectric smoke alarms provide adequate warning for all types of fires and have been shown to be far less likely to be deactivated by occupants."
Although photoelectric alarms are highly effective at detecting smoldering fires and do provide adequate protection from flaming fires, fire safety experts and the NFPA recommend installing what are called combination alarms, which are alarms that either detect both heat and smoke or use both the ionization and photoelectric smoke sensing methods. Some combination alarms may also include a carbon monoxide detection capability.
The type and sensitivity of light source and photoelectric sensor and type of smoke chamber differ between manufacturers.
Carbon monoxide and carbon dioxide detection
Carbon monoxide sensors detect potentially fatal concentrations of carbon monoxide, which may build up due to faulty ventilation where there are combustion appliances such as gas heaters and cookers, although there is no uncontrolled fire outside the appliance.
High levels of carbon dioxide (CO2) may indicate a fire, and can be detected by a carbon dioxide sensor. Such sensors are often used to measure levels of CO2 which may be undesirable but not indicative of a fire. This type of sensor can also be used to detect and warn of the much higher levels of CO2 generated by a fire. Some manufacturers say that detectors based on CO2 levels are the fastest fire indicators and also, unlike ionization and optical detectors, detect fires that do not generate smoke, such as those fuelled by alcohol or gasoline. CO2 detectors are not susceptible to false alarms due to particles making them particularly suitable for use in dusty and dirty environments.
A presentation by Siemens and the Canadian Fire Alarm Association reports that the ionization detector is the best at detecting incipient-stage fires with invisibly small particles, fast-flaming fires with smaller 0.01-0.4 micron particles, and dark or black smoke, while more modern photoelectric detectors are best at detecting slow-smouldering fires with larger 0.4–10.0 micron particles, and light-coloured white/grey smoke.
Photoelectric smoke detectors respond faster to fire that is in its early, smoldering stage. The smoke from the smouldering stage of a fire is typically made up of large combustion particles between 0.3 and 10.0 µm. Ionization smoke detectors respond faster (typically 30–60 seconds) to the flaming stage of a fire. The smoke from the flaming stage of a fire is typically made up of microscopic combustion particles between 0.01 and 0.3 µm. Also, ionization detectors are weaker in high air flow environments and because of this, the photoelectric smoke detector is more reliable for detecting smoke in both the smoldering and flaming stages of a fire.
In June 2006, the Australian Fire & Emergency Service Authorities Council, the peak representative body for all Australian and New Zealand fire departments, published an official report, 'Position on Smoke Alarms in Residential Accommodation'. Clause 3.0 states, "Ionization smoke alarms may not operate in time to alert occupants to escape from a smoldering fire."
In August 2008, the International Association of Fire Fighters (IAFF) passed a resolution recommending the use of photoelectric smoke alarms, saying that changing to photoelectric alarms "Will drastically reduce the loss of life among citizens and firefighters."
In May 2011, the Fire Protection Association of Australia’s (FPAA) official position on smoke alarms stated, "The Fire Prevention Association of Australia considers that all residential buildings should be fitted with photoelectric smoke alarms..."
In December 2011, the Volunteer Firefighter's Association of Australia published a World Fire Safety Foundation report, 'Ionization Smoke Alarms are DEADLY', citing research outlining substantial performance differences between ionization and photoelectric technology.
In November 2013, the Ohio Fire Chiefs' Association (OFCA) published an official position paper supporting the use of photoelectric technology in Ohioan residences. The OFCA's position states, "In the interest of public safety and to protect the public from the deadly effects of smoke and fire, the Ohio Fire Chiefs' Association endorses the use of photoelectric smoke alarms in both new construction and when replacing old smoke alarms or purchasing new alarms."
In June 2014, tests by the Northeastern Ohio Fire Prevention Association (NEOFPA) on residential smoke alarms were broadcast on ABC's ‘Good Morning America’ program. The NEOFPA tests showed ionization smoke alarms were failing to activate in the early, smoldering stage of a fire. The combination ionization/photoelectric alarms failed to activate for an average of over 20 minutes after the stand-alone photoelectric smoke alarms. This vindicated the June 2006 official position of the Australasian Fire & Emergency Service Authorities Council (AFAC) and the October 2008 official position of the International Association of Fire Fighters (IAFF). Both the AFAC and the IAFF recommend photoelectric smoke alarms, but not combination ionization/photoelectric smoke alarms.
Due to the varying levels of detection capabilities between detector types, manufacturers have designed multi-criteria devices which cross-reference the separate signals to both rule out false alarms and improve response times to real fires.
Obscuration is a unit of measurement that has become the standard way of specifying smoke detector sensitivity. Obscuration is the effect smoke has that reduces light intensity, expressed in percent absorption per unit length; higher concentrations of smoke result in higher obscuration levels.
|Ionization||2.6–5.0% obs/m (0.8–1.5% obs/ft)|
|Photoelectric||0.70–13.0% obs/m (0.2–4.0% obs/ft)|
|Aspirating||0.005–20.5% obs/m (0.0015–6.25% obs/ft)|
|Laser||0.06–6.41% obs/m (0.02–2.0% obs/ft)|
Commercial smoke detectors are either conventional or addressable, and are connected to security alarm or fire alarm systems controlled by fire alarm control panels (FACP). These are the most common type of detector, and are usually significantly more expensive than single-station battery-operated residential smoke alarms. They are used in most commercial and industrial facilities and other places such as ships and trains, but are also part of some security alarm systems in homes. These detectors don't need to have built in alarms, as alarm systems can be controlled by the connected FACP, which will set off relevant alarms, and can also implement complex functions such as a staged evacuation.
The word "conventional" is slang used to distinguish the method used to communicate with the control unit in newer addressable systems. So called "conventional detectors" are smoke detectors used in older interconnected systems and resemble electrical switches by their way of working. These detectors are connected in parallel to the signaling path so that the current flow is monitored to indicate a closure of the circuit path by any connected detector when smoke or other similar environmental stimulus sufficiently influences any detector. The resulting increase in current flow (or a dead short) is interpreted and processed by the control unit as a confirmation of the presence of smoke and a fire alarm signal is generated. In a conventional system, smoke detectors are typically wired together in each zone and a single fire alarm control panel usually monitors a number of zones which can be arranged to correspond to different areas of a building. In the event of a fire, the control panel is able to identify which zone or zones contain the detector or detectors in alarm, but can not identify which individual detector or detectors are in a state of alarm.
An addressable system gives each detector an individual number, or address. Addressable systems allow the exact location of an alarm to be plotted on the FACP, while allowing several detectors to be connected to the same zone. In certain systems, a graphical representation of the building is provided on the screen of the FACP which shows the locations of all of the detectors in the building, while in others the address and location of the detector or detectors in alarm are simply indicated.
Addressable systems are usually more expensive than conventional non-addressable systems, and offer extra options, including a custom level of sensitivity (sometimes called Day/Night mode) which can determine the amount of smoke in a given area and contamination detection from the FACP that allows determination of a wide range of faults in detection capabilities of smoke detectors. Detectors become contaminated usually as a result of the build up of atmospheric particulates in the detectors being circulated by the heating and air-conditioning systems in buildings. Other causes include carpentry, sanding, painting, and smoke in the event of a fire. Panels can also be interconnected to monitor a very large number of detectors in multiple buildings. This is most commonly used in hospitals, universities, resorts and other large centres or institutions.
Smaller, less expensive, smoke alarm systems, typically used in a domestic/residential environment, may be individual standalone units, or interconnected. They typically generate a loud acoustic warning signal as their only action. Several detectors (whether standalone or interconnected) are normally used in the rooms of a dwelling. There are inexpensive smoke alarms that may be interconnected so that any detector that triggers sounds all alarms. They are powered by mains electricity, with disposable or rechargeable battery backup. They may be interconnected by wires, or wirelessly. They are required in new installations in some jurisdictions.
- Audible tones
- Spoken voice alert
- Visual strobe lights
- 177 candela output
- Emergency light for illumination
- Tactile stimulation (e.g. bed or pillow shaker), although no standards existed as of 2008 for tactile stimulation alarm devices.
Some models have a hush or temporary silence feature that allows silencing, typically by pressing a button on the housing, without removing the battery. This is especially useful in locations where false alarms can be relatively common (e.g. near a kitchen), or users might remove the battery permanently to avoid the annoyance of false alarms, preventing the alarm from detecting a fire should one break out.
While current technology is very effective at detecting smoke and fire conditions, the deaf and hard of hearing community has raised concerns about the effectiveness of the alerting function in awakening sleeping individuals in certain high-risk groups such as the elderly, those with hearing loss and those who are intoxicated. Between 2005 and 2007 research sponsored by the United States' National Fire Protection Association (NFPA) focused on understanding the cause of the higher number of deaths in such high-risk groups. Initial research into the effectiveness of the various alerting methods is sparse. Research findings suggest that a low frequency (520 Hz) square wave output is significantly more effective at awakening high risk individuals. Wireless smoke and carbon monoxide detectors linked to alert mechanisms such as vibrating pillow pads for the hearing impaired, strobes, and remote warning handsets are more effective at waking people with serious hearing loss than other alarms.
Batteries are used either as sole or as backup power for residential smoke detectors. Mains-operated detectors have disposable or rechargeable batteries; others run only on 9-volt disposable batteries. When the battery is exhausted a battery-only smoke detector becomes inactive; most smoke detectors chirp repeatedly if the battery is low. It has been found that battery-powered smoke detectors in many houses have dead batteries. It has been estimated[when?] that in the UK over 30% of smoke alarms have dead or removed batteries. In response public information campaigns have been created to remind people to change smoke detector batteries regularly. In Australia, for example, a public information campaign suggests that smoke alarm batteries should be replaced on April Fools' Day every year. In regions using daylight saving time, campaigns may suggest that people change their batteries when they change their clocks or on a birthday.
Some mains-powered detectors are fitted with a non-rechargeable lithium battery for backup with a life of typically ten years, after which it is recommended that the detector be replaced. User-replaceable disposable 9-volt lithium batteries, which last at least twice as long as alkaline batteries are available.
The US National Fire Protection Association recommends that home-owners replace smoke detector batteries with a new battery at least once per year, when it starts chirping (a signal that the battery is low), or when it fails a test, which the NFPA recommends to be carried out at least once per month by pressing the "test" button on the alarm.
A 2004 NIST report concluded that "Smoke alarms of either the ionization type or the photoelectric type consistently provided time for occupants to escape from most residential fires," and, "Consistent with prior findings, ionization type alarms provided somewhat better response to flaming fires than photoelectric alarms (57 to 62 seconds faster response), and photoelectric alarms provided (often) considerably faster response to smoldering fires than ionization type alarms (47 to 53 minutes faster response)."
Regular cleaning can prevent false alarms caused by the build-up of dust and insects, particularly on optical type alarms as they are more susceptible to these factors. A vacuum cleaner can be used to clean domestic smoke detectors to remove detrimental dust. Optical detectors are less susceptible to false alarms in locations such as near a kitchen producing cooking fumes.
On the night of May 31, 2001, Bill Hackert and his daughter Christine of Rotterdam, New York died when their house caught fire and a First Alert ionization smoke detector failed to sound. The cause of the fire was a frayed electrical cord behind a couch that smoldered for hours before engulfing the house with flames and smoke. The ionization smoke detector was found to be defectively designed, and in 2006 a jury in the United States District Court for the Northern District of New York decided that First Alert and its then parent company, BRK Brands, was liable for millions of dollars in damages.
Installation and placement
In the United States most state and local laws regarding the required number and placement of smoke detectors are based upon standards established in NFPA 72, National Fire Alarm and Signaling Code. Laws governing the installation of smoke detectors vary depending on the locality. However, some rules and guidelines for existing homes are relatively consistent throughout the developed world. For example, Canada and Australia require a building to have a working smoke detector on every level. The United States NFPA code cited in the previous paragraph requires smoke detectors on every habitable level and within the vicinity of all bedrooms. Habitable levels include attics that are tall enough to allow access. Many other countries have comparable requirements.
In new construction, minimum requirements are typically more stringent. All smoke detectors must be hooked directly to the electrical wiring, be interconnected and have a battery backup. In addition, smoke detectors are required either inside or outside every bedroom, depending on local codes. Smoke detectors on the outside will detect fires more quickly, assuming the fire does not begin in the bedroom, but the sound of the alarm will be reduced and may not wake some people. Some areas also require smoke detectors in stairways, main hallways and garages.
A dozen or more detectors may be connected via wiring or wirelessly such that if one detects smoke, the alarms will sound on all the detectors in the network, improving the likelihood that occupants will be alerted even if smoke is detected far from their location. Wired interconnection are more practical in new construction than for existing buildings.
In the UK the installation of smoke alarms in new builds must comply with British Standard BS5839 pt6. BS 5839: Pt.6: 2004 recommends that a new-build property consisting of no more than 3 floors (less than 200 square metres per floor) should be fitted with a Grade D, LD2 system. Building Regulations in England, Wales and Scotland recommend that BS 5839: Pt.6 should be followed, but as a minimum a Grade D, LD3 system should be installed. Building Regulations in Northern Ireland require a Grade D, LD2 system to be installed, with smoke alarms fitted in the escape routes and the main living room and a heat alarm in the kitchen; this standard also requires all detectors to have a mains supply and a battery back up.
EN54 European standards
Fire detection products have the European Standard EN 54 Fire Detection and Fire Alarm Systems that is a mandatory standard for every product that is going to be delivered and installed in any country in the European Union (EU). EN 54 part 7 is the standard for smoke detectors. European standard are developed to allow free movement of goods in the European Union countries. EN 54 is widely recognized around the world. The EN 54 certification of each device must be issued annually.
Coverage of smoke and temperature detectors with European standard EN54
|Surface area (square meters)||Type of detector||Height (m)||Ceiling slope ≤20°||Ceiling slope >20°|
|Smax(square meters)||Rmax (m)||Smax (square meters)||Rmax(m)|
|6< h ≤ 12||80||6,6||110||9,6|
|SA ≤30||EN54-5 Clase A1||≤7,5||30||4,4||30||5,7|
|EN54-5 Clase A2,B,C,D,F,G||≤ 6||30||4,4||30||5,7|
|SA >30||EN54-5 Clase A1||≤7,5||20||3,5||40||6,5|
|EN54-5 Clase A2,B,C,D,E,F,G||≤6||20||3,5||40||6,5|
- EN54-7: Smoke detector
- EN54-5: Temperature detector
- SA: Surface area
- Smax (square meters): Maximum surface coverage
- Rmax (m): Maximum radio
Information that is in bold is the standard coverage of the detector. Smoke detector coverage is 60 square meters and temperature smoke detector coverage is 20 square meters. The height from the ground is an important issue for correct protection.
An additional (harmonised) EN14604 also exists, which tends to be the standard usually cited at domestic point of sale. This standard expands on the EN54 recommendations for domestic smoke alarms and specifies requirements, test methods, performance criteria, and manufacturer's instructions. It also includes additional requirements for smoke alarms, which are suitable for use in leisure accommodation vehicles.  However, much of EN14604 is voluntary. A study published 2014 assessed six areas of compliance & found 33% of devices claiming to meet this standard did not do so in one or more of the specifics. The study also found 19% of the products to have a problem with actual fire detection.
Australia and United States
In the United States, the first standard for home smoke alarms was established in 1967. In 1969, the AEC allowed homeowners to use smoke detectors without a license. The Life Safety Code (NFPA 101), passed by the National Fire Protection Association in 1976, first required smoke alarms in homes. Smoke alarm sensitivity requirements in UL 217 were modified in 1985 to reduce susceptibility to nuisance alarms. In 1988 BOCA, ICBO, and SBCCI model building codes begin requiring smoke alarms to be interconnected and located in all sleeping rooms. In 1989 NFPA 74 first required smoke alarms to be interconnected in every new home construction, and in 1993 NFPA 72 first required that smoke alarms be installed in all bedrooms. The NFPA began requiring the replacement of smoke detectors after ten years in 1999. In 1999, Underwriters Laboratory (UL) changed smoke alarm labeling requirements so that all smoke alarms must have a manufactured date written in plain English.
In June 2013, a World Fire Safety Foundation report titled, 'Can Australian and U.S. Smoke Alarm Standards be Trusted?' was published in the official magazine of the Australian Volunteer Firefighter Association. The report brings into question the validity of testing criteria used by American and Australian government agencies when undergoing scientific testing of ionization smoke alarms in smoldering fires.
In June 2010 the City of Albany, California, enacted a photoelectric only legislation after a unanimous decision by the Albany City Council; several other Californian and Ohioan cities enacted similar legislation shortly afterwards.
In November 2011, the Northern Territory enacted Australia's first residential photoelectric legislation mandating the use of photoelectric smoke alarms in all new Northern Territory homes.
From January 1, 2017 in the Australian state of Queensland, all smoke alarms in new dwellings (or where a dwelling is substantially renovated) must be photoelectric, not also contain an ionization sensor, be hardwired to the mains power supply with a secondary power source (i.e. battery), and be interconnected with every other smoke alarm in the dwelling so all activate together. From that date, all replacement smoke alarms must be photoelectric; from January 1, 2022, all dwellings sold, leased, or where a lease is renewed must comply as for new dwellings; and from January 1, 2027, all dwellings must comply as for new dwellings.
In June 2013, in an Australian Parliamentary speech, the question was asked, "Are ionization smoke alarms defective?" This was further to the Australian Government's scientific testing agency (the Commonwealth Scientific and Industrial Research Organisation - CSIRO) data revealing serious performance problems with ionization technology in the early, smoldering stage of a fire, a rise in litigation involving ionization smoke alarms, and increasing legislation mandating the installation of photoelectric smoke alarms. The speech cited in May 2013, World Fire Safety Foundation report published in the Australian Volunteer Firefighter Association's magazine titled, 'Can Australian and U.S. Smoke Alarm Standards be Trusted?' The speech concluded with a request for one of the world's largest ionization smoke alarm manufacturers and the CSIRO to disclose the level of visible smoke required to trigger the manufacturers' ionization smoke alarms under CSIRO scientific testing. The US state of California banned the sale of smoke detectors with replaceable batteries.
- "Smoke Alarms in U.S. Home Fires". nfpa.org. September 2015. Archived from the original on 2017-07-29. Retrieved 2017-07-28.
- US 436961, Francis Robbins Upton
- "Birthday Party to Edison; Men Associated with Him in the Early 80s Organize the Pioneers" (PDF). The New York Times. February 3, 1918. Retrieved January 13, 2011.
Francis R. Upton of Newark, Mr. Edison's oldest associate, has been elected President of the Pioneers.
- GB 190225805, George Andrew Darby, "An Electric Heat-indicator and Fire-alarm"
- Prosser, Richard (1970). Birmingham Inventors And Inventions. H.M. Patent Office (originally 1881) later published by S.R. Publishers 1970. ISBN 0-85409-578-0.
- "NRC: Fact Sheet on Smoke Detectors". NRC.gov. United States Nuclear Regulation Commission. 4 September 2013. Archived from the original on 27 July 2014. Retrieved 9 June 2014.
- Wallis, Ian (1 November 2013). 50 Best Business Ideas That Changed the World. Jaico Publishing House. ISBN 9788184952841. Retrieved 2014-11-20.
- "How smoke detector is made". MadeHow.com. Advameg. Archived from the original on 7 June 2014. Retrieved 9 June 2014.
- Jones, Hilton Ira (April 1955). "Peeps at Things to Come". The Rotarian. Rotary International. 86 (4). Archived from the original on 2018-05-08. Retrieved 2014-11-27.
- White Paper: Home Smoke Alarms and Other Fire Detection and Alarm Equipment (Technical report). Public/Private Fire Safety Council. 2006. 1.
- "History of Smoke Detectors". The Daily Secure. Retrieved 2020-12-27.
- Ha, Peter (25 October 2010). "Smoke Detector". Time. Time (ALL-TIME 100 Gadgets): 1. Archived from the original on 14 July 2014. Retrieved 9 June 2014.
- "Voluntary Standards and Accreditation Act of 1977". Act No. S. 825 of 1 March 1977. Retrieved 24 July 2014.
- David Lucht (1 March 2013). "Where Theres Smoke". Nfpa.org. Archived from the original on 20 December 2015. Retrieved 7 January 2016. With picture of SmokeGard
- US patent 3863076, Donald F. Steele & Robert B. Enemark, "Optical Smoke Detector", issued 1975-01-28
- Fleming, Jay. "Smoke Detector Technology Research" Archived 2016-04-20 at the Wayback Machine, retrieved 2011-11-07
- Cote, Arthur; Bugbee, Percy (1988). "Ionization smoke detectors". Principles of fire protection. Quincy, MA: National Fire Protection Association. p. 249. ISBN 0-87765-345-3.
- Residential Smoke Alarm Performance, Thomas Cleary, Building and Fire Research Laboratory, National Institute of Standards and Technology, UL Smoke and Fire Dynamics Seminar. November, 2007.
- "Performance of Home Smoke Alarms Analysis of the Response of Several Available Technologies in Residential Fire Settings". Bukowski, Cleary et al. Archived from the original on 2010-08-22.
- "NuDat 2.1 database". NNDC.BNL.gov. Brookhaven National Laboratory. Archived from the original on 2012-03-11.
- "Smoke detectors and americium-241 fact sheet" (PDF). Canadian Nuclear Society. Archived (PDF) from the original on 2011-07-06. Retrieved 2009-08-31.
- Gerberding, Julie Louise (April 2004). "Toxicological Profile for Americium" (PDF; 2.1MiB). United States Department of Health and Human Services/Agency for Toxic Substances and Disease Registry. Archived (PDF) from the original on 2009-09-06. Retrieved 2009-08-29.
- "Disposing of Smoke Detectors | Radiation Protection | US EPA". EPA. 27 June 2012. Archived from the original on 2 June 2013. Retrieved 2013-06-26.
- "Safe disposal of smoke alarms - Fire and Rescue NSW". NSW Government. 26 November 2012. Archived from the original on 20 April 2013. Retrieved 2013-06-26.
- "Lycée Blaise Pascal Rouen - Smoke alarms". pascal-lyc.spip.ac-rouen.fr. Retrieved 2015-12-28.
- "Smoke Alarms in the Home" (PDF). CFPA-E.eu. Confederation of Fire Protection Associations in Europe. 2008. p. 5. Archived (PDF) from the original on 2015-05-11. Retrieved 2015-05-11.
- Brazzell, D. "The Effects of High Air Velocity and Complex Airflow Patterns on Smoke Detector Performance" (PDF). AFCOM8-21.AFCOM-Miami-Admin.com. Archived from the original (PDF) on 2012-03-20. Retrieved 2009-05-13.
- New York City Fire Department. "Carbon monoxide alarms" (PDF). Archived (PDF) from the original on 2012-01-31. Retrieved 2012-05-28.
- "Carbon Dioxide - Life and Death" (PDF). senseair.se. p. 4. Retrieved 2018-12-21.
- Smoke Detector Sensitivity testing: Siemens and Canadian Fire Alarm Association Archived 2016-02-22 at the Wayback Machine
- "Fire and Life Safety in Mission-Critical Applications". Life Safety Magazine. Archived from the original on April 16, 2012. Retrieved 2011-07-01.[failed verification]
- "Position on Smoke Alarms in Residential Accommodation" (PDF). Australasian Fire & Emergency Service Authorities Council. Archived from the original (PDF) on 2012-12-24. Retrieved 2006-06-01.
- "International Association of Fire Fighters Resolution 15". The International Association of Fire Fighters, California, USA. Archived from the original on 2013-08-28. Retrieved 2013-06-27.
- "Position Statement - Selection of Residential Smoke Alarms - clause 5.0, page 7, May, 2011" (PDF). Fire Protection Association Australia. Archived (PDF) from the original on 2013-05-10. Retrieved 2013-06-27.
- "Ionization Smoke Alarms Are DEADLY". The World Fire Safety Foundation. Archived from the original on 2014-04-16. Retrieved 2001-06-27.
- "OFCA Position Statement on Smoke Alarms" (PDF). Ohio Fire Chief's Association. Archived (PDF) from the original on 2014-10-06. Retrieved 2014-10-03.
- "'GMA' Investigates: Will Your Smoke Detector Respond Fast Enough?". Good Morning America. Archived from the original on 2014-09-03. Retrieved 2014-05-29.
- "Smoke Alarm Myths Explained". The World Fire Safety Foundation. Archived from the original on 2014-10-06. Retrieved 2014-09-03.
- "Low-Profile Plug-in Intelligent Laser Smoke Detector" (PDF). SystemSensor.com. Archived (PDF) from the original on 2014-05-02. Retrieved 2014-05-01.
- "Fire Alarm System" (PDF). ssspl.org. Archived (PDF) from the original on 29 August 2017. Retrieved 8 May 2018.
- Fisher, Jeff. "Adding Smoke Detectors to a Security System". Wiki.hometech.com. TechWiki. Archived from the original on 14 July 2014. Retrieved 6 June 2014.
- "Addressable Equipment". Westminster International Ltd. Archived from the original on 2009-11-24. Retrieved 2010-06-09.
- "Contaminated (dirty) Smoke Detectors". Firewize.com. Firewize Holdings Pty. 2012. Archived from the original on 29 July 2014. Retrieved 6 June 2014.
- Nest Labs (17 June 2015). "Why are interconnected smoke alarms better than standalone smoke alarms?". Nest Web site. Archived from the original on 4 March 2016. Retrieved 7 January 2016.
- Underwriters Laboratories 217. "Single and Multiple Station Smoke Alarms, UL 1971: Signaling Devices for the Hearing Impaired, UL 268: Smoke Detectors for Fire Alarm Signaling Systems". Cite journal requires
- "Alarm concern from the Hearing Loss Association of America". hearingloss.org. Archived from the original on 27 September 2007. Retrieved 8 May 2018.
- "All about Hearing Loss". www.hearinglossweb.com. Archived from the original on 18 June 2010. Retrieved 8 May 2018.
- Beacham, Janine. "Don't be a fool: change alarm batteries". Augusta Margaret River Mail. Archived from the original on 3 April 2011. Retrieved 19 April 2011.
- "SMOKE ALARM SAFETY TIPS". Safety Information. National Fire Protection Association. Archived from the original on 2009-08-21. Retrieved 2009-05-17.
- "Cleaning Smoke and Heat Alarms". SDFireAlarms.co.uk. Hav Direct. 2011. Archived from the original on 2015-09-25. Retrieved 2015-07-31.
- Segall, Bob (April 2, 2008). "Federal appeals court upholds $2.8M award for faulty smoke alarm". WTHR.com. WTHR. Archived from the original on December 7, 2008. Retrieved 2008-10-28.
- "NFPA 72". Act No. 72-2013 of 2013 (PDF). Archived (PDF) from the original on 22 September 2014. Retrieved 6 August 2014.
- Fletcher, Gregory (18 May 2011). Residential Construction Academy: House Wiring. Technology & Engineering. ISBN 978-1111306212. Archived from the original on 8 May 2018. Retrieved 24 November 2014.
- "BS 5839-6:2013 Fire detection and fire alarm systems for buildings - Code of practice for the design, installation, commissioning and maintenance of fire detection and fire alarm systems in domestic premises". Act No. 5839-6 of 2013. Archived from the original on 2 December 2014. Retrieved 24 November 2014.
- "CEN - Technical Bodies". Cen.eu. 2012-11-11. Archived from the original on 2013-05-20. Retrieved 2014-08-22.
- "BS EN 54-11:2001 - Fire detection and fire alarm systems. Manual call points – BSI British Standards". Shop.bsigroup.com. Archived from the original on 2014-10-18. Retrieved 2014-08-22.
- "Archived copy" (PDF). Archived (PDF) from the original on 2013-11-03. Retrieved 2013-08-26.CS1 maint: archived copy as title (link)
- "Can Australian and U.S. Smoke Alarm Standards be Trusted?". The World Fire Safety Foundation. Retrieved 2013-06-27.
- "Albany, California Ordinance 2010-06 Photoelectric Specific Requirements". The Albany City Council, Albany, California, USA. Archived from the original on 2012-02-03. Retrieved 2013-06-27.
- "Northern Territory Photoelectric smoke alarm legislation". Northern Territory Fire & Rescue Service. Archived from the original on 2011-10-01. Retrieved 2001-06-27.
- "Archived copy" (PDF). Archived (PDF) from the original on 2017-02-18. Retrieved 2017-02-06.CS1 maint: archived copy as title (link)
- "Smoke Alarms". Hansard - Mr Christopher Gulaptis MP, Private Member's Statements, New South Wales Parliamentary Debates, Legislative Assembly, New South Wales, Australia 20 June 2013, pp.22218. Archived from the original on 29 October 2013. Retrieved 2013-06-26.
- Finney, Michael (29 July 2015). "Law bans sale of smoke detectors with replaceable batteries". abc7news.com. Archived from the original on 3 July 2017. Retrieved 8 May 2018.
|Wikimedia Commons has media related to Smoke detector.|