This article has an unclear citation style.August 2012) (Learn how and when to remove this template message)(
Peaking power plants, also known as peaker plants, and occasionally just "peakers", are power plants that generally run only when there is a high demand, known as peak demand, for electricity. Because they supply power only occasionally, the power supplied commands a much higher price per kilowatt hour than base load power. Peak load power plants are dispatched in combination with base load power plants, which supply a dependable and consistent amount of electricity, to meet the minimum demand.
Peak hours usually occur in the morning or late afternoon/evening depending on location. In temperate climates, peak hours often occur when household appliances are heavily used in the evening after work hours. In hot climates, the peak is usually late afternoon when air conditioning load is high, during this time many workplaces are still open and consuming power. In cold climates, the peak is in the morning when space heating and industry are both starting up.
A peaker plant may operate many hours a day, or it may operate only a few hours per year, depending on the condition of the region's electrical grid. Because of the cost of building an efficient power plant, if a peaker plant is only going to be run for a short or highly variable time, it does not make economic sense to make it as efficient as a base load power plant. In addition, the equipment and fuels used in base load plants are often unsuitable for use in peaker plants because the fluctuating conditions would severely strain the equipment. For these reasons, nuclear, geothermal, waste-to-energy, coal and biomass are rarely, if ever, operated as peaker plants.
For countries that are trending away from coal-fired base load plants and towards intermittent energy sources such as wind and solar, there is a corresponding increase in the need for peaking or load following power plants and the use of a grid intertie.
Peaker plants are generally gas turbines that burn natural gas. A few burn biogas or petroleum-derived liquids, such as diesel oil and jet fuel, but they are generally more expensive than natural gas, so their use is limited to areas not supplied with natural gas. However, many peaker plants are able to use petroleum as a backup fuel, as storing oil in tanks is easy. The thermodynamic efficiency of simple-cycle gas turbine power plants ranges from 20 to 42%, with between 30 and 42% being average for a new plant.
For greater efficiency, a heat recovery steam generator (HRSG) is added at the exhaust. This is known as a combined cycle plant. Cogeneration uses waste exhaust heat for process, district heating or other heating uses. Both of these options are used only in plants that are intended to be operated for longer periods than usual. Natural gas and diesel generators with reciprocating engines are sometimes used for grid support using smaller plants.
Another option for increased efficiency and power output in gas turbines is installing a turbine inlet air cooling system, that cools down the inlet air temperature increasing mass flow ratio. This option, in combination with a thermal energy storage tank, can increase the turbine power output in on-peak periods up to 30%.
Hydroelectric dams are intentionally variable; they can generate less during off-peak and quickly respond to peak demands, consequently hydroelectricity may function as load following or a peaking plant and with sufficient water, a base-load plant. Natural gas turbines or pumped storage are often used where there is not enough hydroelectricity to respond to daily and weekly variations in generation and consumption. It is not unusual for a dam to be built with more capacity than can be sustained by the water supply, allowing for a higher peak output. Upgrading equipment at existing dams can be one of the least expensive ways of increasing peak generation. The ability to vary the amount of electricity generated is often limited by the requirement that minimum or maximum flows downstream are satisfied.
Pumped-storage hydroelectricity is the largest-capacity form of grid energy storage available, used for averaging off-peak and peak electrical demands. The site stores energy using the gravitational potential of water stored in a reservoir. Low-cost off-peak electric power from base load or intermittent sources is used to pump water at a low elevation to storage in a high elevation reservoir. During periods of high electrical demand, the stored water is released through turbines to produce electric power. Start up times are only a few minutes, and some can start in a few tens of seconds.
Batteries are used in some cases where conditions favor it to smooth flow (avoiding a costly power line upgrade) as well as supplying peak power and other grid services such as operating reserve, sometimes in hybrid configuration with turbines or diesel engines. Battery power is by far the fastest responding of all powerplants, and can respond to grid conditions at millisecond timescales, giving slower responding equipment a chance to react to outages.
Pumped-storage and batteries are net consumers, as they have no inherent energy source, and the conversion between electricity and storage and back incurs some losses.
Solar thermal peaker plants were proposed in 2017, under a US Department of Energy Technology 2 Market award to Hank Price of SolarDynamics, whose paper Dispatchable Solar Power Plant proposed utilizing the thermal energy storage inherent in a solar thermal energy power plant, that enables this heat-based form of solar to generate like a gas peaker, to supply power on demand day or night, and in return be controlled by the utility and paid in capacity payments to be available when needed, like a traditional peaker plant. A solar thermal power plant makes electricity in a steam cycle power plant like a traditional power plant but the heat for steam is supplied by solar energy heating a material such as molten salts and storing the heat until needed to make steam for power generation.
Base load power plants
The opposites of peaking plants are base load power plants. Nuclear and coal burning plants operate continuously, stopping only for maintenance or unexpected outages. Intermediate load following power plants such as hydroelectric operate between these extremes, curtailing their output on nights and weekends when demand is low. Base load and intermediate plants are used preferentially to meet electrical demand because the lower efficiencies of peaker plants make them more expensive to operate.
- Geothermal power
- List of energy storage projects
- Smart grid
- Turbine inlet air cooling
- Load following power plant
- Renewable and Efficient Electric Power Systems by Gilbert M. Masters
- "Archived copy". Archived from the original on 2009-11-01. Retrieved 2016-08-22.CS1 maint: Archived copy as title (link)
- https://books.google.ca/books?redir_esc=y&id=M0EnqtFxW3cC&q=peak+time#v=snippet&q=peak%20time&f=false pg 284
- Kamal NA, Zuhair AM (2006). Enhancing gas turbine output through inlet air cooling. Sudan Eng. Soc. J., 52(4-6): 7-14.
- "BPA Balancing Authority Load and Total Wind Generation".
- "California drought leads to less hydropower, increased natural gas generation - Today in Energy - U.S. Energy Information Administration (EIA)".
- "NC DEQ: Instream Flow Unit".
- "Mitsubishi Electric Delivers High-capacity Energy-storage System to Kyushu Electric Power's Buzen Substation". EQ Int'l Magazine. 4 March 2016. Retrieved 24 January 2017.
The facility offers energy-storage capabilities similar to those of pumped hydro facilities while helping to improve the balance of supply and demand
- Lambert, Fred (23 January 2017). "Tesla quietly brings online its massive – biggest in the world – 80 MWh Powerpack station with Southern California Edison". Electrek. Retrieved 24 January 2017.
capacity of 20 MW/80 MWh . the system will charge using electricity from the grid during off-peak hours, when demand is low, and then deliver electricity during peak hours
- Shallenberger, Krysti (30 November 2015). "5 battery energy storage projects to watch in 2016". Utility Dive. Retrieved 24 January 2017.
manage demand during peak periods, provide reliable back-up power, and reduce their peak demand charges during the day. The project also aims to sell frequency regulation . The utility is leveraging multiple value streams
- "Inside GE and SoCal Edison's First-of-a-Kind Hybrid Peaker Plant With Batteries and Gas Turbines". 2017-04-18. Retrieved 19 April 2017.
two hybrid electric gas turbine (EGT) units . Each peaker plant is in the 50-megawatt range, and is outfitted with a set of batteries capable of providing 10 megawatts and 4 megawatt-hours of power. the trick here is how you coordinate the control system, so from the grid operation standpoint, you see a black box that delivers power how they need it, when they need it
- "Technology to Market | Department of Energy". energy.gov. Retrieved 2018-01-09.
- Price, Hank. "Dispatchable Solar Power Plant" (PDF). http://www.solarpaces.org. Retrieved 8 January 2018. External link in
- "Archived copy". Archived from the original on 2009-10-31. Retrieved 2016-08-22.CS1 maint: Archived copy as title (link)