Hard water is water that has high mineral content (in contrast with "soft water"). Hard water is formed when water percolates through deposits of limestone, chalk or gypsum which are largely made up of calcium and magnesium carbonates, bicarbonates and sulfates.
Hard drinking water may have moderate health benefits. It can pose critical problems in industrial settings, where water hardness is monitored to avoid costly breakdowns in boilers, cooling towers, and other equipment that handles water. In domestic settings, hard water is often indicated by a lack of foam formation when soap is agitated in water, and by the formation of limescale in kettles and water heaters. Wherever water hardness is a concern, water softening is commonly used to reduce hard water's adverse effects.
Natural rainwater, snow and other forms of precipitation typically have low concentrations of multivalent cations such as Calcium and Magnesium. They may have small concentrations of ions such as Sodium, Chloride and Sulphate derived from wind action over the sea. Where precipitation falls in drainage basin that are formed of hard, impervious and calcium-poor rocks, only very low concentrations of multivalent cations are found and the water is termed Soft water. Examples in the UK (United Kingdom) include Snowdonia in Wales and the Western Highlands in Scotland.
The permanent hardness of water is determined by the concentration of multivalent cations in the water. Multivalent cations are positively charged metal complexes with a charge greater than 1+. Usually, the cations have the charge of 2+. Common cations found in hard water include Ca2+ and Mg2+. These ions enter a water supply by leaching from minerals within an aquifer. Common calcium-containing minerals are calcite and gypsum. A common magnesium mineral is dolomite (which also contains calcium). Rainwater and distilled water are soft, because they contain few ions.
- CaCO3 (s) + CO2 (aq) + H2O (l) ⇌ Ca2+ (aq) + 2 HCO−
The reaction can go in either direction. Rain containing dissolved carbon dioxide can react with calcium carbonate and carry calcium ions away with it. The calcium carbonate may be re-deposited as calcite as the carbon dioxide is lost to atmosphere, sometimes forming stalactites and stalagmites.
Calcium and magnesium ions can sometimes be removed by water softeners.
Permanent hardness (mineral content) is generally difficult to remove by boiling. If this occurs, it is usually caused by the presence of calcium sulfate/calcium chloride and/or magnesium sulfate/magnesium chloride in the water, which do not precipitate out as the temperature increases. Ions causing permanent hardness of water can be removed using a water softener, or ion-exchange column.
Temporary hardness is caused by the presence of dissolved bicarbonate minerals (calcium bicarbonate and magnesium bicarbonate). When dissolved, these type of minerals yield calcium and magnesium cations (Ca2+, Mg2+) and carbonate and bicarbonate anions (CO2−
3 and HCO−
3). The presence of the metal cations makes the water hard. However, unlike the permanent hardness caused by sulfate and chloride compounds, this "temporary" hardness can be reduced either by boiling the water, or by the addition of lime (calcium hydroxide) through the process of lime softening. Boiling promotes the formation of carbonate from the bicarbonate and precipitates calcium carbonate out of solution, leaving water that is softer upon cooling.
With hard water, soap solutions form a white precipitate (soap scum) instead of producing lather, because the 2+ ions destroy the surfactant properties of the soap by forming a solid precipitate (the soap scum). A major component of such scum is calcium stearate, which arises from sodium stearate, the main component of soap:
- 2 C17H35COO− (aq) + Ca2+ (aq) → (C17H35COO)2Ca (s)
Hardness can thus be defined as the soap-consuming capacity of a water sample, or the capacity of precipitation of soap as a characteristic property of water that prevents the lathering of soap. Synthetic detergents do not form such scums.
Because soft water has few calcium ions, there is no inhibition of the lathering action of soaps and no soap scum is formed in normal washing. Similarly, soft water produces no calcium deposits in water heating systems.
Hard water also forms deposits that clog plumbing. These deposits, called "scale", are composed mainly of calcium carbonate (CaCO3), magnesium hydroxide (Mg(OH)2), and calcium sulfate (CaSO4). Calcium and magnesium carbonates tend to be deposited as off-white solids on the inside surfaces of pipes and heat exchangers. This precipitation (formation of an insoluble solid) is principally caused by thermal decomposition of bicarbonate ions but also happens in cases where the carbonate ion is at saturation concentration. The resulting build-up of scale restricts the flow of water in pipes. In boilers, the deposits impair the flow of heat into water, reducing the heating efficiency and allowing the metal boiler components to overheat. In a pressurized system, this overheating can lead to failure of the boiler. The damage caused by calcium carbonate deposits varies on the crystalline form, for example, calcite or aragonite.
The presence of ions in an electrolyte, in this case, hard water, can also lead to galvanic corrosion, in which one metal will preferentially corrode when in contact with another type of metal, when both are in contact with an electrolyte. The softening of hard water by ion exchange does not increase its corrosivity per se. Similarly, where lead plumbing is in use, softened water does not substantially increase plumbo-solvency.
In swimming pools, hard water is manifested by a turbid, or cloudy (milky), appearance to the water. Calcium and magnesium hydroxides are both soluble in water. The solubility of the hydroxides of the alkaline-earth metals to which calcium and magnesium belong (group 2 of the periodic table) increases moving down the column. Aqueous solutions of these metal hydroxides absorb carbon dioxide from the air, forming the insoluble carbonates, giving rise to the turbidity. This often results from the pH being excessively high (pH > 7.6). Hence, a common solution to the problem is, while maintaining the chlorine concentration at the proper level, to lower the pH by the addition of hydrochloric acid, the optimum value being in the range of 7.2 to 7.6.
It is often desirable to soften hard water. Most detergents contain ingredients that counteract the effects of hard water on the surfactants. For this reason, water softening is often unnecessary. Where softening is practised, it is often recommended to soften only the water sent to domestic hot water systems so as to prevent or delay inefficiencies and damage due to scale formation in water heaters. A common method for water softening involves the use of ion-exchange resins, which replace ions like Ca2+ by twice the number of mono cations such as sodium or potassium ions.
The World Health Organization says that "there does not appear to be any convincing evidence that water hardness causes adverse health effects in humans". In fact, the United States National Research Council has found that hard water actually serves as a dietary supplement for calcium and magnesium.
Some studies have shown a weak inverse relationship between water hardness and cardiovascular disease in men, up to a level of 170 mg calcium carbonate per litre of water. The World Health Organization has reviewed the evidence and concluded the data was inadequate to allow for a recommendation for a level of hardness.
Recommendations have been made for the maximum and minimum levels of calcium (40–80 ppm) and magnesium (20–30 ppm) in drinking water, and a total hardness expressed as the sum of the calcium and magnesium concentrations of 2–4 mmol/L.
The Softened-Water Eczema Trial (SWET), a multicenter randomized controlled trial of ion-exchange softeners for treating childhood eczema, was undertaken in 2008. However, no meaningful difference in symptom relief was found between children with access to a home water softener and those without.
Hardness can be quantified by instrumental analysis. The total water hardness is the sum of the molar concentrations of Ca2+ and Mg2+, in mol/L or mmol/L units. Although water hardness usually measures only the total concentrations of calcium and magnesium (the two most prevalent divalent metal ions), iron, aluminium, and manganese can also be present at elevated levels in some locations. The presence of iron characteristically confers a brownish (rust-like) colour to the calcification, instead of white (the color of most of the other compounds).
Water hardness is often not expressed as a molar concentration, but rather in various units, such as degrees of general hardness (dGH), German degrees (°dH), parts per million (ppm, mg/L, or American degrees), grains per gallon (gpg), English degrees (°e, e, or °Clark), or French degrees (°fH, °f or °HF; lowercase f is used to prevent confusion with degrees Fahrenheit). The table below shows conversion factors between the various units.
Hardness unit conversion. 1 mmol/L 1 ppm, mg/L 1 dGH, °dH 1 gpg 1 °e, °Clark 1 °fH mmol/L 1 0.009991 0.1783 0.171 0.1424 0.09991 ppm, mg/L 100.1 1 17.85 17.12 14.25 10 dGH, °dH 5.608 0.05603 1 0.9591 0.7986 0.5603 gpg 5.847 0.05842 1.043 1 0.8327 0.5842 °e, °Clark 7.022 0.07016 1.252 1.201 1 0.7016 °fH 10.01 0.1 1.785 1.712 1.425 1
The various alternative units represent an equivalent mass of calcium oxide (CaO) or calcium carbonate (CaCO3) that, when dissolved in a unit volume of pure water, would result in the same total molar concentration of Mg2+ and Ca2+. The different conversion factors arise from the fact that equivalent masses of calcium oxide and calcium carbonates differ, and that different mass and volume units are used. The units are as follows:
- Parts per million (ppm) is usually defined as 1 mg/L CaCO3 (the definition used below). It is equivalent to mg/L without chemical compound specified, and to American degree.
- Grains per Gallon (gpg) is defined as 1 grain (64.8 mg) of calcium carbonate per U.S. gallon (3.79 litres), or 17.118 ppm.
- a mmol/L is equivalent to 100.09 mg/L CaCO3 or 40.08 mg/L Ca2+.
- A degree of General Hardness (dGH or 'German degree (°dH, deutsche Härte))' is defined as 10 mg/L CaO or 17.848 ppm.
- A Clark degree (°Clark) or English degrees (°e or e) is defined as one grain (64.8 mg) of CaCO3 per Imperial gallon (4.55 litres) of water, equivalent to 14.254 ppm.
- A French degree (°fH or °f) is defined as 10 mg/L CaCO3, equivalent to 10 ppm.
As it is the precise mixture of minerals dissolved in the water, together with the water's pH and temperature, that determine the behavior of the hardness, a single-number scale does not adequately describe hardness. However, the United States Geological Survey uses the following classification , hard and soft water,
Classification hardness in mg-CaCO3/L hardness in mmol/L hardness in dGH/°dH hardness in gpg hardness in ppm Soft 0–60 0–0.60 0–3.37 0–3.50 0–60 Moderately hard 61–120 0.61–1.20 3.38–6.74 3.56–7.01 61–120 Hard 121–180 1.21–1.80 6.75–10.11 7.06–10.51 121–180 Very hard ≥ 181 ≥ 1.81 ≥ 10.12 ≥ 10.57 ≥ 181
Seawater is considered to be very hard due to various dissolved salts. Typically seawater's hardness is in the area of 6,630 ppm (6.63 grams per litre). In contrast, freshwater has hardness in the range of 15 to 375 ppm.
Several indices are used to describe the behaviour of calcium carbonate in water, oil, or gas mixtures.
Langelier saturation index (LSI)
The Langelier saturation index (sometimes Langelier stability index) is a calculated number used to predict the calcium carbonate stability of water. It indicates whether the water will precipitate, dissolve, or be in equilibrium with calcium carbonate. In 1936, Wilfred Langelier developed a method for predicting the pH at which water is saturated in calcium carbonate (called pHs). The LSI is expressed as the difference between the actual system pH and the saturation pH:
- LSI = pH (measured) − pHs
- For LSI > 0, water is super saturated and tends to precipitate a scale layer of CaCO3.
- For LSI = 0, water is saturated (in equilibrium) with CaCO3. A scale layer of CaCO3 is neither precipitated nor dissolved.
- For LSI < 0, water is under saturated and tends to dissolve solid CaCO3.
If the actual pH of the water is below the calculated saturation pH, the LSI is negative and the water has a very limited scaling potential. If the actual pH exceeds pHs, the LSI is positive, and being supersaturated with CaCO3, the water has a tendency to form scale. At increasing positive index values, the scaling potential increases.
In practice, water with an LSI between −0.5 and +0.5 will not display enhanced mineral dissolving or scale forming properties. Water with an LSI below −0.5 tends to exhibit noticeably increased dissolving abilities while water with an LSI above +0.5 tends to exhibit noticeably increased scale forming properties.
The LSI is temperature sensitive. The LSI becomes more positive as the water temperature increases. This has particular implications in situations where well water is used. The temperature of the water when it first exits the well is often significantly lower than the temperature inside the building served by the well or at the laboratory where the LSI measurement is made. This increase in temperature can cause scaling, especially in cases such as hot water heaters. Conversely, systems that reduce water temperature will have less scaling.
- Water Analysis:
- pH = 7.5
- TDS = 320 mg/L
- Calcium = 150 mg/L (or ppm) as CaCO3
- Alkalinity = 34 mg/L (or ppm) as CaCO3
- LSI formula:
- LSI = pH − pHs
- pHs = (9.3 + A + B) − (C + D) where:
- A = log10[TDS] − 1/ = 0.15
- B = −13.12 × log10(°C + 273) + 34.55 = 2.09 at 25 °C and 1.09 at 82 °C
- C = log10[Ca2+ as CaCO3] - 0.4 = 1.78
- (Ca2+ as CaCO3 is also called calcium hardness, and is calculated as 2.5[Ca2+])
- D = log10[alkalinity as CaCO3] = 1.53
Ryznar Stability Index (RSI)
Ryznar saturation index (RSI) was developed from empirical observations of corrosion rates and film formation in steel mains. It is defined as:
- RSI = 2 pHs – pH (measured)
- For 6.5 < RSI < 7 water is considered to be approximately at saturation equilibrium with calcium carbonate
- For RSI > 8 water is under saturated and, therefore, would tend to dissolve any existing solid CaCO3
- For RSI < 6.5 water tends to be scale form
Puckorius Scaling Index (PSI)
The Puckorius Scaling Index (PSI) uses slightly different parameters to quantify the relationship between the saturation state of the water and the amount of limescale deposited.
The hardness of local water supplies depends on the source of water. Water in streams flowing over volcanic (igneous) rocks will be soft, while water from boreholes drilled into porous rock is normally very hard.
Analysis of water hardness in major Australian cities by the Australian Water Association shows a range from very soft (Melbourne) to hard (Adelaide). Total hardness levels of calcium carbonate in ppm are:
- Canberra: 40; Melbourne: 10–26; Sydney: 39.4–60.1; Perth: 29–226; Brisbane: 100; Adelaide: 134–148; Hobart: 5.8–34.4; Darwin: 31.
Prairie provinces (mainly Saskatchewan and Manitoba) contain high quantities of calcium and magnesium, often as dolomite, which are readily soluble in the groundwater that contains high concentrations of trapped carbon dioxide from the last glaciation. In these parts of Canada, the total hardness in ppm of calcium carbonate equivalent frequently exceed 200 ppm, if groundwater is the only source of potable water. The west coast, by contrast, has unusually soft water, derived mainly from mountain lakes fed by glaciers and snowmelt.
Some typical values are:
- Montreal 116 ppm, Calgary 165 ppm, Regina 496 ppm, Saskatoon 160–180 ppm, Winnipeg 77 ppm, Toronto 121 ppm, Vancouver < 3 ppm, Charlottetown, PEI 140–150 ppm, Waterloo Region 400 ppm, Guelph 460 ppm, Saint John (West) 160–200 ppm, Ottawa 30 ppm.
In England and Wales
Hardness water level of major cities in the UK Area Primary source Level Manchester Lake District (Haweswater, Thirlmere) Pennines (Longdendale Chain) 1.750 °clark / 25 ppm Birmingham Elan Valley Reservoirs 3 °clark /
Bristol Mendip Hills (Bristol Reservoirs) 16 °clark / 228.5 ppm Southampton Bewl Water 18.76 °clark / 268 ppm London (EC1A) Lee Valley Reservoir Chain 19.3 °clark / 275 ppm
Information from the British Drinking Water Inspectorate shows that drinking water in England is generally considered to be 'very hard', with most areas of England, particularly east of a line between the Severn and Tees estuaries, exhibiting above 200 ppm for the calcium carbonate equivalent. Water in London, for example, is mostly obtained from the River Thames and River Lea both of which derive significant proportion of their dry weather flow from springs in limestone and chalk aquifers. Wales, Devon, Cornwall and parts of northwest England are softer water areas, and range from 0 to 200 ppm. In the brewing industry in England and Wales, water is often deliberately hardened with gypsum in the process of Burtonisation.
Generally water is mostly hard in urban areas of England where soft water sources are unavailable. A number of cities built water supply sources in the 18th century as the industrial revolution and urban population burgeoned. Manchester was a notable such city in North West England and its wealthy corporation built a number of reservoirs at Thirlmere and Haweswater in the Lake District to the north. There is no exposure to limestone or chalk in their headwaters and consequently the water in Manchester is rated as 'very soft'. Similarly, tap water in Birmingham is also soft as it is sourced from the Elan Valley Reservoirs in Wales, even though groundwater in the area is hard.
The EPA has published a standards handbook for the interpretation of water quality in Ireland in which definitions of water hardness are given. In this section, reference to original EU documentation is given, which sets out no limit for hardness. In turn, the handbook also gives no "Recommended or Mandatory Limit Values" for hardness. The handbooks does indicate that above the midpoint of the ranges defined as "Moderately Hard", effects are seen increasingly: "The chief disadvantages of hard waters are that they neutralise the lathering power of soap.... and, more important, that they can cause blockage of pipes and severely reduced boiler efficiency because of scale formation. These effects will increase as the hardness rises to and beyond 200 mg/l CaCO3."
In the United States
A collection of data from the United States found that about half the water stations tested had hardness over 120 mg per litre of calcium carbonate equivalent, placing them in the categories "hard" or "very hard". The other half were classified as soft or moderately hard. More than 85% of American homes have hard water. The softest waters occur in parts of the New England, South Atlantic-Gulf, Pacific Northwest, and Hawaii regions. Moderately hard waters are common in many of the rivers of the Tennessee, Great Lakes, and Alaska regions. Hard and very hard waters are found in some of the streams in most of the regions throughout the country. The hardest waters (greater than 1,000 ppm) are in streams in Texas, New Mexico, Kansas, Arizona, Utah, parts of Colorado, southern Nevada, and southern California.
- "Hard water". National Groundwater Association. Retrieved 28 June 2019.
- World Health Organization Hardness in Drinking-Water, 2003
- Weingärtner, Herman] (December 2006). Ullmann's Encyclopedia of Industrial Chemistry - Water. Weinheim: Wiley–VCH. doi:10.1002/14356007.a28_001.
- "Map showing the rate of hardness in mg/l as Calcium carbonate in England and Wales" (PDF). DEFRA/ Drinking Water Inspectorate. 2009.
- USGS - U.S. Geological Survey Office of Water Quality. "USGS Water-Quality Information: Water Hardness and Alkalinity". usgs.gov.
- Christian Nitsch, Hans-Joachim Heitland, Horst Marsen, Hans-Joachim Schlüussler, "Cleansing Agents" in Ullmann's Encyclopedia of Industrial Chemistry 2005, Wiley–VCH, Weinheim. doi:10.1002/14356007.a07_137
- Sengupta, Pallav (August 2013). "Potential Health Impacts of Hard Water". International Journal of Preventive Medicine. 4 (8): 866–875. ISSN 2008-7802. PMC 3775162. PMID 24049611.
- "Lime Softening". Retrieved 4 November 2011.
- Wisconisin DNR - Carbonate chemistry
- Stephen Lower (July 2007). "Hard water and water softening". Retrieved 2007-10-08.
- PP Coetzee (1998). "Scale reduction and scale modification effects induced by Zn" (PDF). Archived from the original (PDF) on 2016-05-09. Retrieved 2010-03-29.
- Sorg, Thomas J.; Schock, Michael R.; Lytle, Darren A. (August 1999). "Ion Exchange Softening: Effects on Metal Concentrations". Journal AWWA. 91 (8): 85–97. doi:10.1002/j.1551-8833.1999.tb08685.x. ISSN 1551-8833. Archived from the original on 2011-07-26. Retrieved 2010-11-23.
- "Drinking Water Hardwater Hardness Calcium Magnesium Scale Stained Laundry". Water-research.net. Retrieved 2013-01-26.
- František Kožíšek Health significance of drinking water calcium and magnesium Archived 2013-04-18 at the Wayback Machine, February 2003
- Pocock SJ, Shaper AG, Packham RF (April 1981). "Studies of water quality and cardiovascular disease in the United Kingdom". Sci. Total Environ. 18: 25–34. Bibcode:1981ScTEn..18...25P. doi:10.1016/S0048-9697(81)80047-2. PMID 7233165.
- Marque S, Jacqmin-Gadda H, Dartigues JF, Commenges D (2003). "Cardiovascular mortality and calcium and magnesium in drinking water: an ecological study in elderly people" (PDF). Eur. J. Epidemiol. 18 (4): 305–9. doi:10.1023/A:1023618728056. PMID 12803370. S2CID 1834547.
- Rubenowitz E, Axelsson G, Rylander R (January 1999). "Magnesium and calcium in drinking water and death from acute myocardial infarction in women". Epidemiology. 10 (1): 31–6. doi:10.1097/00001648-199901000-00007. PMID 9888277.
- McNally NJ, Williams HC, Phillips DR, Smallman-Raynor M, Lewis S, Venn A, Britton J (1998). "Atopic eczema and domestic water hardness". The Lancet. 352 (9127): 527–531. doi:10.1016/S0140-6736(98)01402-0. PMID 9716057. S2CID 6319959.
- Miyake Y, Yokoyama T, Yura A, Iki M, Shimizu T (Jan 2004). "Ecological association of water hardness with prevalence of childhood atopic dermatitis in a Japanese urban area". Environ. Res. 94 (1): 33–7. Bibcode:2004ER.....94...33M. doi:10.1016/S0013-9351(03)00068-9. PMID 14643284.
- Arnedo-Pena A, Bellido-Blasco J, Puig-Barbera J, Artero-Civera A, Campos-Cruañes JB, Pac-Sa MR, Villamarín-Vázquez JL, Felis-Dauder C (2007). "Domestic water hardness and prevalence of atopic eczema in Castellon (Spain) school children". Salud Pública de México. 49 (4): 295–301. doi:10.1590/S0036-36342007000400009. PMID 17710278.
- Perkin MR, Craven J, Logan K, Strachan D, Marrs T, Radulovic S, Campbell LE, MacCallum SF, McLean WH, Lack G, Flohr C, Enquiring About Tolerance Study Team (2016). "Association between domestic water hardness, chlorine, and atopic dermatitis risk in early life: A population-based cross-sectional study" (PDF). J Allergy Clin Immunol. 138 (2): 509–516. doi:10.1016/j.jaci.2016.03.031. PMID 27241890.
- A multicentre randomized controlled trial of ion-exchange water softeners for the treatment of eczema in children: protocol for the Softened Water Eczema Trial (SWET) (ISRCTN: 71423189) http://www.swet-trial.co.uk/
- "Water Hardness". thekrib.com.
- Total water hardness[permanent dead link]
- Corrosion by water Archived 2007-10-20 at the Wayback Machine
- McTigue, Nancy E.; Symons, James M., eds. (2011). The Water Dictionary: A Comprehensive Reference of Water Terminology. American Water Works Association. pp. 333–. ISBN 978-1-61300-101-1.
- Reid, Robert N. (2003). Water Quality Systems: Guide For Facility Managers. CRC Press. pp. 66–. ISBN 978-0-8247-4010-8.
- Langelier, W. F. (October 1936). "The Analytical Control of Anti-Corrosion Water Treatment". Journal of the American Water Works Association. 28 (10): 1500–1521. doi:10.1002/j.1551-8833.1936.tb13785.x. JSTOR 41226418.
- Aquaprox, ed. (2009). Treatment of cooling water. Springer. pp. 104–. ISBN 978-3-642-01985-2.
- Emerson, A. G. D. (2003). Quantitative Forecasting of Problems in Industrial Water Systems. World Scientific. pp. 7–. ISBN 978-981-238-184-2.
- Ryznar, John W.; Langelier, W. F. (April 1944). "A New Index for Determining Amount of Calcium Carbonate Scale Formed by a Water". Journal of the American Water Works Association. 36 (4): 472–486. doi:10.1002/j.1551-8833.1944.tb20016.x. JSTOR 23345279.
- T.E., Larson and R. V. Skold, Laboratory Studies Relating Mineral Quality of Water to Corrosion of Steel and Cast Iron, 1958 Illinois State Water Survey, Champaign, IL pp.  — 46: ill. ISWS C-71
- Stiff, Jr., H.A., Davis, L.E., A Method For Predicting The Tendency of Oil Field Water to Deposit Calcium Carbonate, Pet. Trans. AIME 195;213 (1952).
- Oddo, J.E., Tomson, M.B., Scale Control, Prediction and Treatment Or How Companies Evaluate A Scaling Problem and What They Do Wrong, CORROSION/92, Paper No. 34, (Houston, TX:NACE INTERNATIONAL 1992). KK
- "Dishwasher and water hardness - Canberra water quality - About Us". actewagl.com.au. Archived from the original on 2012-03-26.
- melbournewater.com.au (PDF) https://web.archive.org/web/20130511163534/http://www.melbournewater.com.au/content/library/publications/reports/compliance_reports/public_health_compliance_quarter_1_(july-september_2006).pdf. Archived from the original (PDF) on 2013-05-11. Retrieved 2006-12-17. Missing or empty
- "Sydney Typical Drinking Water Analysis". Archived from the original on 2013-01-16. Retrieved 2006-12-17.
- "Water Corporation of WA - 404" (PDF). watercorporation.com.au. Archived from the original (PDF) on 2007-09-04.
- "Brisbane Drinking Water". Archived from the original on 2007-11-02. Retrieved 2006-12-17.
- "Adelaide Water Quality". Archived from the original on 2013-03-15. Retrieved 2012-11-30.
- "Hobart City Council, Tasmania Australia". hobartcity.com.au. Archived from the original on 2008-02-10.
- "Darwin Water Quality" (PDF). Archived from the original (PDF) on 2007-09-30. Retrieved 2006-12-17.
- "Ville de Montréal - L'eau de Montréal". .ville.montreal.qc.ca. 2013-01-22. Retrieved 2013-01-26.
- Canadian Water Quality Association. "Water Hardness/Total Households Canadian Cities" (PDF). Archived from the original (PDF) on 4 October 2013. Retrieved 4 October 2013.
- "Frequently Asked Questions". Saskatoon.ca. Retrieved 2013-01-26.
- 2006 Winnipeg drinking water quality test results
- "Water - Services - Living In Toronto - City of Toronto". toronto.ca. 2017-07-14.
- GVRD Wash Smart – Water Facts
- "CITY OF CHARLOTTETOWN WATER & SEWER UTILITY Water Report 2006" (PDF). Aquasafecanada.com. Retrieved 2013-01-26.[permanent dead link]
- "REGION OF WATERLOO Residential Water Softener Performance Study Testing Report #1 April, 2011" (PDF). Regionofwaterloo.ca. Archived from the original (PDF) on 2017-10-13. Retrieved 2013-01-26.
- "Public Information Notice: West Side Water Supply | Saint John". www.saintjohn.ca. Retrieved 2017-10-10.
- Public Works and Environmental Services Dept. (2019-05-07). "Drinking water - Frequently asked questions". ottawa.ca. Retrieved 2020-06-19.
- "Table 2 Drinking Water Hardness". United Utilities. Archived from the original on 2012-04-13. Retrieved 2012-03-03.
- "Drinking water quality". United Utilities. Retrieved 2012-03-03.
- "Severn Trent Water — B1 1DB". Severn Trent Water. Archived from the original on 2012-05-03. Retrieved 2012-03-03.
- "Bristol water hardness level". Bristol Water. Archived from the original on 2011-08-01. Retrieved 2012-03-03.
- "Southern Water — SO14 area". Southern Water. Archived from the original on 2012-11-23. Retrieved 2012-03-03.
- "EC1A 7BE — Water quality in your area". Thames Water. Archived from the original on 2012-05-27. Retrieved 2012-03-03.
- Section 36 "Hardness" https://www.epa.ie/pubs/advice/water/quality/Water_Quality.pdf
- Wilson, Amber; Parrott, Kathleen; Ross, Blake (June 1999). "Household Water Quality – Water Hardness". Retrieved 2009-04-26.
- Briggs, J.C., and Ficke, J.F.; Quality of Rivers of the United States, 1975 Water Year -- Based on the National Stream Quality Accounting Network (NASQAN): U.S. Geological Survey Open-File Report 78-200, 436 p. (1977)
- "Got Hard Water? Here's What You Need To Know About It". Modern Home Pulse. 2018-01-22. Retrieved 2018-09-22.